Honeywell MS-5UD User Manual
When audible devices are sounding, Operating instructions
WHEN AUDIBLE DEVICES ARE SOUNDING -
FOR AN ALARM
1. Evacuate the protected area
2. Notify the monitoring service and/or the Fire Department immediately. Tell them briefly what happened and what
your current status is.
Phones: ____________________________ _________________________________
Fire Department Monitoring Service
3. If the Fire Department is responding, be prepared to provide directions to arriving firefighters.
FOR TROUBLE, SUPERVISORY, AND EMERGENCY ALARMS
1. Notify the monitoring service and/or applicable first responders if this panel is connected to either one, and tell them
what is happening.
2. Silence audible devices by unlocking and opening the panel and pressing the ACKNOWLEDGE/STEP button. The
applicable indicator will remain illuminated. Contact authorized service personnel immediately! (See Below).
DO NOT ALLOW TROUBLE CONDITIONS TO REMAIN LOGGED IN THE SYSTEM.
THE PROTECTION THE SYSTEM OFFERS HAS BEEN COMPROMISED OR ELIMINATED, WHEN A
TROUBLE CONDITION EXISTS.
To return to normal after an alarm
1. Do not enter the protected area until safe to do so.
2. Clear all initiating devices. Smoke detectors will not reset
if there is still smoke in the area.
3. Reset the control panel (PRESS the RESET button)
Power failure or brownout
If AC power drops too low or fails, AC POWER indicator will
extinguish, the system TROUBLE indicator will turn on yellow, and
the panel buzzer and any other audible trouble devices will sound.
Contact authorized service personnel immediately. See below.
Manual activation (Fire Drill or otherwise)
Notification Appliance Circuits (NACs) can be activated by
pressing and holding the DRILL button for at least two
NOTE: You may want to disconnect the municipal box by
sliding the DISCONNECT switch, located on the 4XTMF
module, to its disconnect position (to the right). If a
DACT is connected, notify the monitoring service
before conducting any fire drills or tests.
MS-5UD-3, MS-5UD-3E, MS-5UD-7, MS-5UD-7E, MS-5UD-7C, MS-10UD-3,
MS-10UD-3E, MS-10UD-7, MS-10UD-7E, MS-10UD-7C
Fire Alarm Control Panel
PANEL KEY - The key to open the panel can be found at the
NORMAL - Only AC POWER is illuminated green.
All other indicators are off. LCD display will read SYSTEM
Document #52805 Rev. B 2/7/2011 ECN 10-008
THIS SHEET SHALL BE FRAMED ADJACENT TO
THE CONTROL PANEL
To test the indicators, LCD display and piezo
Press and release the RESET button and check all indicators/
LEDs. Every indicator/LED should be on, LCD shows all pixels
on, piezo sounder beeps.
For more information, refer to the MS-5UD & MS-10UD Series
Manual, Document #52626. It is kept in the following location:
Notification Appliance Circuits may be silenced by pressing the
ALARM SILENCE button. ALARM SILENCED will turn on yellow.
Subsequent alarms will reactivate circuits. Press the RESET
button to clear the "silenced" condition.
NOTE: Notification Appliance Circuits may be programmed as
nonsilenceable. Also, Signal Silence Inhibit, if enabled, will
prevent silencing of NACs for one minute after an alarm (see
Telephone Number: ________________________
In the event of trouble, contact the
local Fire-Lite Service Representative