Honeywell Smoke Alarm User Manual
1 of 15
Fire-Lite IPDACT Setup for Installing Dealers
These pictorial instructions should be used in conjunction with the formal
PID (Product Installation Document) included with the IPBRKT or IPENC as
well as the instructions included with the IPDACT. Please Read all
documentation prior to performing any installation or programming.
Installation Instructions for use with HyperTerminal™ and serial port
Internet Communicator-Contact ID only.
Requires compatible FL panel equipped
with on-board or optional DACT. Requires
300mA aux non-reset able power from
FACP. Includes cable from panel primary
telco port to IPDACT.
Bracket for mounting IPDACT inside MS-
9200UDLS common enclosure or in
optional HPP-300ULX power supply
Splitter for dual phone lines to IPDACT
RJ45-DB9F PC serial port programming
cable for IPDACT.
Optional cabinet for mounting IPDACT next
to compatible Fire-Lite FACP. Use when
connecting to older non common enclosure
panels such as MS-9200UD or MS-9600.
Includes IPBRKT mounting bracket already
Optional UL listed Fire Aux power supply for
mounting IPDACT next to compatible Fire
Panel when additional power is required for