I.C.E. IMR-130 HBR User Manual
I.C.E. (US), INC.
capacity and configuration shall be as detailed on the drawings. The unit shall be CGA and ETL
certified and listed to be in compliance with the current ANSI Z83.18 standard.
The line burner, gas train and controls are to be in accordance with (ANSI) (FM) (IRI) (FM and IRI)
requirements. Both burner and blower shall be compensated for altitude of operation.
The unit is to be completely factory test fired to verify proper operation. The unit capacity is to be
validated with an instantaneous flow meter. A complete electrical circuit analysis is to be conducted
and all systems operated and measured. A combustion analyzer is to be employed while unit is
operating at full capacity to verify combustion emissions. Burner combustion must be clean and
odorless and no aliphatic aldahydes are to be detectable. Combustion efficiency must limit the
products of combustion to a maximum of 5 ppm carbon monoxide and 0.5 ppm nitrogen dioxide.
incorporate a full base pan supported by an integral welded channel iron base. Bases are to be of
industrial welded structural iron integrity, formed sheet metal bases are unacceptable. All
structural iron base supports are to be treated with an industrial epoxy primer enriched with a rust
To ensure the casings are airtight and weatherproof, all panels are to be caulked during assembly.
All casings are to be hand fitted and secured with gasketed self-‐tapping tek screws. Roof casing are
to feature three-‐break standing seam panel design. Roof casings are to be sloped on outdoor units
to prevent standing water. Sloped roofs are to be ¼ in. per foot and feature full drain troughs.
Entire unit casing and accessories are to be insulated with fiberglass insulation with hard neoprene
facing. (1 or 2 in. thick 1-‐1/2# or 2# density) insulation is to be secured with industrial glue and
welded pin spots. Insulation is to be certified to fire and flamespread ratings as outlined by the
ANSI code. The entire floor of the unit is to feature a steel liner sandwiching the insulation.
Units are to be equipped with access doors to all serviceable components. Access doors are to have
full-‐length stainless steel piano hinges. All access doors are to be equipped with an insulation liner,
positive seal latches and gasketing . Access doors are to open outward on negative pressure
sections and inward on positive pressure sections. Access doors to feature 6 in. handles with
locking roller mechanism for ease of latching. All outdoor unit access doors are to be equipped with
Units are to be finished with an industrial grade chain stop alkyd enamel paint. The medium grey
finish coat is to be a mimum of 3 mils thick and provide 100% coverage.