GE 50726 GE Rocker Single Pole Switch White User Manual
GE Accessories for electrical
Attention! The text in this document has been recognized automatically. To view the original document, you can use the "Original mode".
Instructions for 120VAC/15A MAX
Single Pole Switches with
Pressure-Lock® terminals for use on 15 Amp
branch circuits with No. 14 AWG solid copper
conductors only. Do not use on 20A
branch circuit. Screw terminals for use
with No. 12 or 14 AWG copper wire.
power to the
circuit at fuse
box or circuit
plate and test
to be sure
2) Remove old
wall box and
3) For screw terminals, strip off
3/4" of insulation from the ends of the
wires. Reconnect wires to HOT terminals
on new switch, forming wire clockwise
3/4 around screw as shown.
For push-in terminals, strip off 1/2" of
insulation and insert into the push-in
To release Push-In
wires, insert screwdriver into release slot
and pull out wire while applying
4) Connect GREEN
wire to GREEN
screw on switch
5) Tighten all
to 14 in-lbs. Install
switch in wall box.
Replace wall plate.