GE 18218 GE Rocker Single Pole Switch Ivory User Manual
GE Accessories for electrical
Attention! The text in this document has been recognized automatically. To view the original document, you can use the "Original mode".
Instructions for 120VAC/15A MAX
Single Pole Switches with
Pressure-Lock® (Push-In) &
Pressure-Lak® terminals for use on 15 Amp
branch circuitswith No. W AWG solid copper
conductors only. Do not use on 20A
branch circuit. Screw terminals for use
with No. 12 or 10 AWG copper wire.
II Shut off
power to the
circuit at fuse
box or circuit
plate and test
to be sure
21 Remove old
wall box and
31 For screw terminals, strip off
3/4 ■ of insulation from the ends of the
wires. Reconnectwiresto FIOT terminals
on new switch, forming wireclocl«/ise
3/4 around screw os shown.
For push-in terminals, strip off 1/2" of
insulation and insert into the push-in
terminals. NOTE; To release Push-In
wires, insert screwdriver into release slot
and pull outwirewhile applying
4| Connect GREEN
wire to GREEN
screw on switch
5) Tighten oil
to 14 in-lbs Install
switch inwall box.
Replace wall plate.