Notifier RM-1 User Manual
DN-6728:B • 7/28/2010 — Page 1 of 2
Remote Microphone and Cabinets
RM-1, RM-1SA, CAB-RM, CAB-RMR
Emergency Voice Evacuation
RM-1 Series Remote Microphone provides a cost-
effective microphone interface for paging to selected speaker
zones. The Power and Trouble LEDs provide easy-to-under-
stand visual indications of its status. Various mounting
options are available. The microphone assembly can be
mounted in a small, compact enclosure or located in a com-
prehensive paging command center.
The RM-1 Series remote microphone can be utilized with the
DVC Digital Voice Command Center and DAA2 amplifiers,
or to expand a legacy installation.
• Automatic gain control circuit.
• Supervised microphone.
• Form-C trouble contacts.
• Form-C contacts activated when microphone is in use.
• Power On LED.
• Trouble LED.
• Pluggable terminal blocks.
• Low-level audio (LLA) IN and THRU screws.
CAB-3/CAB-4 SERIES INSTALLATION
The RM-1 can mount to the back of an ADP-4B dress panel
inside a CAB-3 or CAB-4 Series cabinet. It can be mounted
in any of the four positions on the dress panel, with the fol-
• Do NOT mount the RM-1 in front of a CHS-4L chassis.
See page 2 for illustrations of mounted units.
Power requirements: 20 mA primary, non-fire alarm cur-
rent; 66 mA when microphone is activated; 20 mA secondary,
non-fire alarm current.
Operating voltage: 17 to 26.4 volts.
PRODUCT LINE INFORMATION
RM-1: Remote microphone assembly for mounting on an
ADP-4B dress panel.
RM-1SA: Remote microphone assembly for mounting in a
CAB-RM(R), for remote applications.
CAB-RM: Stand-alone cabinet, black.
CAB-RMR: Stand-alone cabinet, red.
AGENCY LISTINGS AND APPROVALS
These listings and approvals apply to the RM-1 Series
Remote Microphone. In some cases, certain modules may
not be listed by certain approval agencies, or listing may be
in process. Consult factory for latest listing status.
ULC: CS118/CS733 Vol. 12
MEA: 327-94-E Vol.III
CSFM: 7165-0028:0224 (NFS-3030/NFS2-3030)
FM: Approved (RM-1, RM-1SA)
FDNY: #6058 (NFS2-3030)