Honeywell Smoke Alarm User Manual
3 of 15
2. Mount the IPDACT onto the IPBRKT using the plastic standoffs that came
with the IPBRKT. Screw the standoff through the holes on the IPDACT
into the metal mating threaded standoffs on the IPBRKT. Note, discard
any double sided tape plastic standoffs that may be included with the
IPDACT and use the supplied machine screw versions.
3. Connect 24 VDC from the non-resettable power output of the control panel
to the IPDACT terminals marked "GND" and "+12/24VDC". Be careful to
observe correct polarity! Run the two conductor power supply wire
through the small ferrite ring supplied with the IPDACT.