Honeywell Smoke Alarm User Manual
4 of 15
4. Loop the 8 PIN cable supplied with the IPDACT once through the large
Ferrite Ring. Note that this cable is NOT used as an Ethernet Cable but to
interconnect the dialer output of the panel to the input of the IPDACT.
Plug the 8 PIN cable supplied with the IPDACT into the Primary DACT
port of the control panel. Connect the other end of this cable to he
IPDACT on terminals marked 'TO AP."
5. Connect the secondary DACT port of the control panel to a standard
unpublished RJ-31X phone jack. Note that if the secondary port on the
FACP is not used for a backup via POTS line, the IPSPLT can be
obtained and used to combine both phone lines. In this case, the cable
supplied with the IPDACT connects to the single connector on the IPSPLT
(See Panel Manual).
6. Plug one end of the IPDACT Programming Cable (PN ALSMSC120
(shown above or equivalent) into the black RJ45 receptacle on the
IPDACT labeled CN1. Plug the other end of this cable into the supplied
RS-232 serial adapter that came with the black cable. Plug the adapter
into a COM port on your computer.
7. Connect one end of a CAT5 LAN cable into the Ethernet receptacle on the
IPDACT as shown below (Green cable) and the other end into an
available port on the customer’s LAN hub or switch.