General information – I.C.E. 3 OSDs User Manual
This Direct Fired OSD Spray/Bake Unit, dual air dual temperature unit is designed to provide make up air to satisfy the
exhaust requirement of the paint spray booth. 100% volume on the spray cycle and 50% volume on the dry cycle. Normal
discharge temperature on spray cycle is between 70
° F and 80° F. Normal discharge temperature on dry cycle is between
° F and 180° F. The sequence of operation and wiring diagram are located in the weather housing on out door units and
burner compartments of indoor unit.
Fire or Explosion hazard can cause property damage, severe injury or death. Ensure that all air taken into the unit is
free from the presence of:
Flammable solids, liquids and gases.
Explosive materials. Example: grain dust, coal dust, gun powder etc.
Substance which may be come toxic when exposed to heat or passing through a gas flame.
INSTALLATION AND SERVICE INSTRUCTIONS
The information provided is a guide to the proper installation, operation and troubleshooting of the unit. Retain the manual
as a reference for operation and maintenance personnel. Should contact with the factory be necessary, provide the unit model
number and serial number. Install and wire the equipment in accordance with the applicable national and local governing
bodies codes. Authorities having jurisdiction should be consulted before making the installation. Local codes may require
additional safety controls and/or interlocks.
Prior to locating the unit check with the authorities having jurisdiction. The unit should be located with clearance to open
access doors and remove filters. Ensure that the unit is installed level. Provide adequate clearance on either side of the unit
to service blower, bearings, motors, drives and filters. Ensure that the position of the heater relative to support beams is
correct so as to provide adequate support for the equipment. For roof mounted units, check the spacing of the roof structure
beams to avoid interference with air ducts.
LOCATION OF ACCESSORIES
The remote panel will be shipped as a separate package. Mount the panel and have an electrical contractor install wiring.
FACTORY TESTING & START UP CHECKLIST
All OSD series units are factory fired and tested prior to shipping. Each unit is shipped with the tester’s report and a start-up
checklist. Complete the start-up checklist and return one copy to the factory.