Cp-100 optional indoor control panel – Pentair EasyTouch Pool/Spa Control System LX-100EZ User Manual
Rev. F 3-26-04
CP-100 OPTIONAL INDOOR CONTROL PANEL
If the system has an Indoor Controller, verify that there is a TEMPERATURE Display and check that the
EQUIPMENT STATUS INDICATORS are functioning when the Push-buttons are activated.
If there is no status display, check the connections at each end of the communication cables very carefully. If necessary,
crimp new modular connectors to the cables.
If the TEMPERATURE Display indicates three dashes (- - -) or a very high temperature (400 degrees or more),
check the connections to the Temperature Sensor.
At the Indoor Controller, press appropriate Push-button(s) so that none of the EQUIPMENT STATUS
INDICATORS are illuminated.
At the Indoor Controller, press Push-button #S to turn the spa on.
Verify that the Valve Actuators have rotated to spa circulation, the filter pump has been activated and the heater has
Press Push-buttons #1, #2 and #3, and check that appropriate equipment is being activated.
A set of adhesive labels is provided for custom identification of equipment.
Use a pair of fine-tip tweezers to adhere the appropriate label(s) below the Push-button(s) on the Indoor Controller.
Calibration of the TEMPERATURE Display has been preset at the factory. However, fine adjustment can be
accomplished if necessary.
Insert a small flat-blade screwdriver through the ADJUST hole which is located behind the right door of the Indoor
Controller, and rotate the Adjustment Screw accordingly.
The system is now ready to be operated as desired.