Quest, Installation – Sunlight Supply Quest Dual 155 Overhead Dehumidifier User Manual
Quest 105, 155, and 205 Dual
Installation, Operation and Maintenance Instructions
Asset Protection and IAQ Solutions
The Quest Dual can be installed in a variety of
locations to meet the owner’s needs; other considerations include:
1. Providing access to a 115 VAC power outlet
(10’ power cord is provided).
2. Locating near a floor or other suitable drain
(8’ drain hose included).
3. Mount 4” above drain.
4. Do not install the Quest Dual with the exhaust of the unit within 1’ of a wall or obstruction. Do not place
the unit near open water.
4.1A No Ducting (fig. 1)
The simplest installation is to place the Quest Dual with no ducting. To ensure optimal performance, the air
inlet and the outlet of the unit must be at least 2’ from walls and other obstructions to air flow. Recirculation
of outlet air into inlet should be avoided as much as possible.
Out put of